How The Pandemic Drives Legionella Concerns
Even before COVID-19, Legionella had the distinction of being one of the leading water-borne disease agents in the USA, with reported cases growing more than five-fold from 2000-2017 (CDC). But now, as COVID-19 and stagnant water due to building closures collide, the threat increases.
What is Legionella?
Legionella bacteria occur naturally in warm, freshwater environments, like lakes and streams. They become problematic to health when they grow in plumbing systems, particularly where biofilm has developed on pipe walls, and then spread as water is distributed throughout the building. To cause infection, Legionella must be aspirated making showerheads, water fountains, cooling towers, and, less commonly, taps and drinking fountains points of contamination. In high risk populations, Legionella infection can cause a serious type of pneumonia. The simplest way to prevent infections is to keep Legionella out of building water systems.
UV Treatment is a proven solution for preventing Legionella contamination of building water systems, and is suitable for:
- Hospitals and healthcare facilities
- Office and commercial buildings
UV can be applied at the point-of-entry as a complementary treatment barrier for the whole building or at point-of-use for high risk areas within a plumbing system. Different species of Legionella require different UV dose levels for inactivation. However, in general, required doses are low and well within the operating parameters of our range of UV systems.
|Legionella Bozemanii||3.5 mJ/cm2||4.7 mJ/cm2||5.83 mJ/cm2|
|Legionella dumoffi||5.5 mJ/cm2||7.33 mJ/cm2||9.17 mJ/cm2|
|Legionella gormanii||4.9 mJ/cm2||6.55 mJ/cm2||8.17 mJ/cm2|
|Legionella micdadei||3.1 mJ/cm2||4.13 mJ/cm2||5.17 mJ/cm2|
(found in potting soil)
|3.8 mJ/cm2||5.1 mJ/cm2||6.33 mJ/cm2|
Routine Legionella testing is not common in the operation and maintenance of many building water systems, with the exception of hospitals and healthcare facilities. But, given the extensive shutdowns and low-level use and occupancy of so many buildings, including schools and offices, testing is strongly encouraged. Where Legionella is detected, the corrective actions include inactivation (thermal or hyper-chlorination) and flushing, followed by repeat testing. UV inactivation can then be employed to avoid re-inoculation of the plumbing system.
Vendée Eau is securing a future supply of drinking water with the Jourdain pilot programme that will recycle treated wastewater to supplement the Jaunay Reservoir Meeting the demand for clean water has never been more challenging. Communities around the world are...
In this episode of Water Talk from Water Online, Andrew Daley from Trojan Technologies discusses UV AOP treatment. This treatment involves using UV light with an oxidant to treat water that has environmental contaminants. Contaminants that this method can treat...
The City of Oceanside, located in Southern California, is like many cities in the region in that most of their drinking water is imported, traveling to the community from hundreds of miles away. Imported water is brought in from the Colorado River and the Bay Delta in...